Fire and Smoke Door Annual Testing Requirements in Health Care Occupancies
The Centers for Medicare & Medicaid Services (CMS) adopted the 2012 edition of the NFPA LSC, which includes requirements for the maintenance, inspection, and testing of fire doors and smoke doors in certain certified health care facilities.
The 2012 LSC added new provisions under Section 188.8.131.52 – Inspection of Door Openings for the annual inspection and testing of certain fire doors and smoke doors assemblies in accordance with the 2010 editions of NFPA 80 – Standard for Fire Doors and Other Opening Protectives, and NFPA 105 – Standard for Smoke Door Assemblies and Other Opening Protectives.
The new LSC provisions under sections 184.108.40.206.1 and 220.127.116.11.2 require certain fire door and smoke door assemblies to be inspected and tested annually in accordance with the NFPA 80 and NFPA 105. However, section 18.104.22.168.1 states that these requirements only apply where required by Chapters 11 through 43. Therefore, as the LSC health care occupancy chapters (i.e., Chapters 18, 19, 20, 21) do not directly reference section 22.214.171.124, these new annual inspection and testing requirement do not apply to health care occupancies.
For more information you can download the memorandum in full here
, or call us at 631-454-9595 for more information. Back to News & Events